Fire alarm control panel is designed to implement a reliable system of fire safety at medium premises (offices, shops, banks, warehouses, etc.).
Optimum functionality and wide range of additional equipment allow to meet the individual fire safety requirements of a particular object, thus simplifying the job of both developing engineer, installer and service personnel.
- Number of alarm loops: 8;
- Voltage in loop in standby mode: 11 - 12,5 V;
- Resistance of alarm loop – no more than 250 Ohms;
- Response time of alarm loop: no more than 0.4 seconds;
- Power consumption from the mains: less than 50 VA;
- Current consumption from the mains: less than 0.23 A;
- Current consumption from the battery, not more (quiescent mode) than 170 mA;
- Current consumption from the battery, not more (alarm mode) than 260 mA;
- Slot for battery: 18 Ah;
- Power supply 220V (-15%,+10%), 50±1 Hz;
- Load on the DET output + 12V, no more than 2A;
- Load on the SIR output, no more than 5A;
- Operating temperatures range: -5°C..+ 40°C;
- Dimensions: 330x410x85 mm.
- Installation Instructions PPCS "Tiras-8P" (version 6, battstart) tiras4p_nv_5_ua_new.pdf (1.78 Mb) Download
- Instruction on exploitation "Tiras-8P" (version 6, battstart) tiras4p_ne_5_ua_new.pdf (755.23 Kb) Download
- Certificate of conformity for fire receiving-control devices "Tiras PRIME 8", "Tiras PRIME 16", "Tiras-4P '," Tiras-4P.1 ",'" Tiras-8P "," Tiras-8P.1 "', "Tiras-16P", "Tiras-16.128P", "Tiras PRIME 8L" as a part according to the appendix sert_convencional.pdf (3.71 Mb) Download
- Certificate of examination equipment and protective systems intended for use in potentially explosive environments. Series: Tiras Р, Tiras PRIME, Tiras-А sc_170201_red_1.pdf (6.48 Mb) Download
- Декларація про відповідність пожежних приладів pozhezhni_prylady.zip (8.95 Mb) Download
For project engineer
- Connection scheme "Tiras-8P" shema8p.zip (107.43 Kb) Download